> End-user empowered - buy from dealer, manage himself> B-BC Listed Controllers (BACnet Building Controller)> 0% to 100% output voltage scaling> Freely programmable - Flexibility - Accuracy - Hover over values - Debugging (reduced commissioning time)> Code stored in the controllers> Templates save time> BVPN security with RC-RA> MPV-L can display any object in the systems (gas, water, etc)> Backward compatibility> Scalable graphics and animations
CBASIC Advantages> Better for complicated tasks> Easier to troubleshoot - saves time on commissioning> Colour-coding of objects is customisable> Timer countdown value ONMOUSEOVER; follow the logic> GOTO should only refer to lines belowFIRMWARE> Operating system for the controller - always free> To update firmware: 1) Login in to Dealer Support 2) FIRMWARE > DOWNLOAD > UNZIP in RC-Toolkit> Then use OS SEND to: - select file to be loaded - select controller to be updated> Enough controller memory to add new firmware while old still running, then replace> Only dealers have access to f/w - never customers> MULTICAST updates f/w via MS/TP on all CTRTRs on a network at once> MPZ, MPA, SSC: pan file removed during update, don't do remotely!
RC Studio> Advanced BACnet workstation> Panel file templates: reduce errors esp. expanding existing buildings> Can send multiple CBAS, Systems Groups> CBAS Editor: create watchlist for variables you hover over> Right-click to watch in real time> Points Reports> Can build system graphic in blank canvas, don't need a JPG to startEnterprise Schedules> Hierarchical: whatever level you schedule at affects everything below it> Works 80% of the time> Other 20% allows hierarchical exceptions, called BLOCKS> Drag items from different places into a BLOCK and schedule as oneRC-Toolkit> For dealers to configure. Not needed by building controllerRC-WebView> Designed as Operator Interface> Will be a server-based and HTML5 Operator Workstation, including: 1) User groups with RULES 2) CBASIC editing with auto-complete: toggle variable in <> on/off 3) Panel file back-up and restore 4) Transfer AlarmsRC Archive> BACnet archiving softwareRC Reporter> DATA SETS: report on a set of data rather than individual points> BLDG7-Rm101-SAT - data set on Rm101 gathers all data on Rm101> New variables (-Rm101-OCC) automatically added to the data setRC-GrafxSet> 4,131 images> 1,638 animations> Need your own authoring toolIFDD (Integrated Fault Detection and Diagnostics)> Most existing FDD solutions are stand-alone, not BMS-integrated> Can add to competitor's system; must have RC-ST3 + MACH controller> Industry has FDD rules/regulations - VPAC, ASHRAE> Rule broked, tile -> RED; click, flip, see broken rule; click rule for fixes> Embedded in RC-GrafxSet - Click logo> 20 Rules - each rule has 21 Tasks> Create new System Group in RC-ST3 for tiles> Configure dB of tiles, right-click, insert animations> Map every rule in a tile to a BINARY VALUE or TASK ARRAY
MPP> Modules connect via IO-Net
MACH-ProLight> Isolated 24V PSU: +ve switch relay ON, -ve switch it OFF> Up to 16 outputs> Terminal unit different to MPZ> Green connector is EnOcean instead of SmartNet which is now on RJ45> Latching relay - triggered by 12VDC and mechanically held in position> Single ON/OFF wire.> Sends pulse back on same wire with relay position - no I/P needed> Can use universal output as relay driver, using a jumper> GE relay not preferred - always PANASONIC.> GE needs 5 wires if you want ON/OFF and STATUS> Factory-built lighting panels will be PANASONIC only> Trafo not grounded - REF terminal connected to Earth/Ground> EnOcean transceiver handles 32 devices with 4 points = 128 objects> EnOcean primarily lighting> Can also deal with LUX, OCC devices and Plug Control> “ET” = EnOcean transceiver> We can switch up to 4 relays at a time> For dimming, fixtures must be 0-10VDC> BLINK WARN: lights blink to warn occupants they will turn off shortly> Photo Sensor to measure LUX
MS/TP> MS/TP = protocol, not physical network: Master-Slave-Token-Passing> MS/TP: “T” = microphone, owner can broadcast, everyone else listens> Sensors daisy-chained on SmartNet or MS/TP: - send packets on same line - controller differentiates based on addresses in the packets
Please select review
Please enter your name
Please insert valid email!
Please write your comment
All reports are strictly confidential. This appears to be: